Twin Heating Cable 63,0 Meter
Twin Heating Cable for Electric Underfloor HeatingThe Mi-Heat Twin Heating Cable is supplied with a 3m long connection cable (PTC thermistor). The twin heating cable has a power consumption of 12W per running meter.
This Mi-Heat Heating Cable is a genie when it comes to unconventional floor forms, e.g. niches, corners, columns, steps, stairs, pedestals, narrow spaces, semicircular spaces, and winter garden etc. The low construction height of mere 4.0mm allows heating cables to be used for renovations or new builds of any kind. The twin technology allows the connection to be made on one side only.
Scope of Application
- room with usual shapes
- for screed
- under tiles
- electric underfloor heating
- and other uses
pre-assembled, with 3 m PTC thermistor cable on one side only
can be installed beneath all floor coverings such as tiles, stone, wood, laminate, carpet, cork, PVC, etc.
completely maintenance-free and wear-free
ideal for rooms of various designs
every Mi-Heat heating cable is subject to strict quality and functional tests
High Quality: manufactured in accordance with the VDE standard -DINEN60335-2-96, DIN EN60335-1 and DIN EN50366. Approval: VDE (heating conductor)
operating voltage: 230V
max. Power consumption: 760Watt
heated area: 5-7,3m² depending on the loop distance
cable diameter: 4,4mm
max. Operating temperature: 80 ° C
length of connection cable: 3.0 meters
IP degree of protection: IP67
1x Mi-Heat Twin heating cable 63 m
1x assembly instructions
Further product information:
Mi-Heat Twin Heating Cable can be installed with a loop distance of 5-12cm. This flexible distance allows you to adjust the heating capacity per m² to your needs. Hence, it’s possible to build certain heating zones. In this case, e.g. in front of the sink or on outside walls the heating cable can be installed with a smaller loop distance. To fix heating calbe please use either adhesive tape, hot glue or mounting adhesive. The loop distance should be at least 5cm.
The Mi-Heat Twin Heating Cable must be operated through a thermostat. The threshold temperature of this thermostat should be at least 30° C.